Using the included mounting bracket, Sense can be mounted either within your electrical panel or external to your panel.
If you do not have room at the bottom of your electrical panel, Sense can be mounted at the top with the included mounting bracket.
The mounting bracket should be mounted internally using flame retardant double-sided tape, such as 3M™ VHB.
Warning: Do not use screws to attach the bracket to your electrical panel. The included mounting screws are for external use only!
If your electrical panel is outdoors, Sense must be protected from the elements in a NEMA-approved enclosure. See the technical specs for temperature and environmental specifications.
To install Sense outside of the electrical panel, you will need to install a 4-prong 120V/240V electric receptacle and mating plug on the supplied power cable (receptacle and plug not included).
Locate an ideal place to install the external mounting bracket. Make sure that all wires are unobstructed and that the 46″ current sensor cables can reach the Sense monitor. Plan to install the hardware no further than 1′ from your electrical panel.
Recommended Receptacle Type: NEMA L14-20R or 14-20R
Recommended Plug Type: NEMA L14-20P or 14-20P
Please wait while you are redirected to the right page...